Main Features of N1C040 Nuheat Cable 40 sq ft kit 120V
- Cable length: 143' ft. feet, or (1716"in. inches)
- Heated area: 40 Sq Ft
- Heat output (BTU): 1640 BTU total
- See all the quality standard features built in to N1C040 Nuheat Cable System.
- Whats’s in the box: N1C040 -
- 25 Year Warranty
- Made in the USA
- N1C040, N1C040
- Instructions + Video
Instructions + Video
Install Steps No Skill Level Running Cable more difficult + more time than MATS. Installation only by qualified persons. Electrician recommended for wiring GFEP / GFCI Protection (Ground Fault Circuit Interrupter) Required for each circuit. Built-in to all Nuheat thermostats. Circuit Breakers and Supply Wire (always follow local code) No Maximum Circuit Load 15 Amps Maximum Circuit Overload Protection 20 A Breaker. Electrical Box Size (Where Mats connect to Thermostat) No Full Length End-to-End ground wire Yes. Heating Wire construction No Repairable Heating Wire Yes, Wire can be repaired. Repair kits and assistance available. Shower Installation Permitted Yes, can be installed in a tiled shower. Installation Layout Map customized for my project Yes - see examples. We provide Layout Maps only for MATS Expected Floor Temperature This is dependent on many factors. A well-insulated floor can ensure better performance. Insulation Recommended Yes; under slabs or framed floors. Cork or similar on top of Concrete Subfloor as thermal break Indoor Installation Only INTERIOR floor heating Application only. Embedded in Mortar only Installation On Sub Floor on TOP of Sub Floor (Plywood, backer board, concrete) Distance from Wax Ring at toilet flange Install 4 - 6 inches away; can be under front of toilet. Approx 20" from wall Trowel Size recommended minimum 3/8" x 1/4". Works for most ceramic tile; verify with tile/mortar manufacturer Trowel type Recommended Heavy Duty Plastic PRO-Trowel Cut Warning No. Never cut the heating elements to shorten Minimum Installation Temperature 50 Degrees F / 10 Degrees C
UPC 620713030066 Voltage 120VAC How to choose 120 or 240 Volt Same Energy efficiency & same Watts/SF. More Sq Footage per circuit with 240v Watts Per SF 12 Watts per Sq Foot Heat Output BTUs per SF 41 BTU per Sq Ft/Hour Heating Power : Total BTU's 1640 BTU total Manufacturer Nuheat Industries Ltd. Brand Name Nuheat Power Lead Type TEW Wire with Stainless Steel ground braid rated to 105 C and 300v max. Power Lead Length 10 Feet Power Lead Wire Gauge (varies by heated area) 18 AWG Packaging Cardboard box Product Thickness No Heating Wire Spacing 3" on center only Minimum Bend Radius No Ohms Reading (resistance value) 31 (Range is 29-34 ohms) Nuheat ohms range is -5% to +10% ZERO* EMF (Electro Magnetic Field) Zero EMF Controls/Thermostat is required for operation Nuheat Floor sensing thermostat Conduit required for Power Leads Conduit is required for Power Leads Length of heating area Feet No Width of heating area Inches No Length of heating area Inches No
- More Details
What's In The Box No Individual Items No Warranty from Manufacturer 25 years Why Helps No Heated Area Size Covered 40 Amp Draw 3.8 Wattage : Total watts 480 watts Size in Inches No Size in Feet No Installation Style Heating Cable secured to floor using cable guides (track). Guides are secured to floor with tape, screws or glue. Custom Size Options None. Standard lengths only. No customization Safety Listing No Canadian Electric Code reference No Cable strap or guides Cable guides are included in the kit BTUs/SF/Hr 1 No BTUs/SF/Hr 2 No BTUs/SF/Hr 3 No Spacing between runs 1 No Spacing between runs 2 No Spacing between runs 3 No Watts Per SF 1 No Watts Per SF 2 No Watts Per SF 3 No Heated SF 1 No Heated SF 2 No Heated SF 3 No Acceptable Floor Coverings Tile, Stone,Granite, Marble, Slate, Engineered wood, Laminate Made In USA Made in Canada from a majority of USA components.
Excellent ProductThis was an excellent product; well done, well packaged, and the installation instructions were complete and clear. Following are some hints that are worth considering:
- We got "cold feet" so to speak and ended up ordering more cable guides since the space we were heating was an irregular shape. Good idea, since they were inexpensive, but...