Main Features of N1C085 Nuheat Cable 85 sq ft kit 120V
- Cable length: 334' ft. feet, or (4008"in. inches)
- Heated area: 85 Sq Ft
- Heat output (BTU): 3485 BTU total
- See all the quality standard features built in to N1C085 Nuheat Cable System.
- Whats’s in the box: N1C085 -
- 25 Year Warranty
- Made in the USA
- N1C085, N1C085
UPC 620713030110 Voltage 120VAC How to choose 120 or 240 Volt Same Energy efficiency & same Watts/SF. More Sq Footage per circuit with 240v Watts Per SF 12 Watts per Sq Foot Heat Output BTUs per SF 41 BTU per Sq Ft/Hour Heating Power : Total BTU's 3485 BTU total Manufacturer Nuheat Industries Ltd. Brand Name Nuheat Power Lead Type TEW Wire with Stainless Steel ground braid rated to 105 C and 300v max. Power Lead Length 10 Feet Power Lead Wire Gauge (varies by heated area) 18 AWG Packaging Cardboard box Heating Wire Spacing 3" on center only Ohms Reading (resistance value) 14 (Range is 13-15 ohms) Nuheat ohms range is -5% to +10% EMF (Electro Magnetic Field) Zero EMF Controls/Thermostat is required for operation Nuheat Floor sensing thermostat Conduit required for Power Leads Conduit is required for Power Leads
- Instructions + Video
Instructions + Video
Instruction Manual Nuheat N1C085 Cable 85 sq ft kit 120V Installation Manual Skill Level Running Cable more difficult + more time than MATS. Installation only by qualified persons. Electrician recommended for wiring GFEP / GFCI Protection (Ground Fault Circuit Interrupter) Required for each circuit. Built-in to all Nuheat thermostats. Maximum Circuit Load 15 Amps Maximum Circuit Overload Protection 20 A Breaker. Full Length End-to-End ground wire Yes. Repairable Heating Wire Yes, Wire can be repaired. Repair kits and assistance available. Shower Installation Yes, can be installed in a tiled shower. Installation Layout Map customized for my project Yes - see examples. We provide Layout Maps only for MATS Expected Floor Temperature This is dependent on many factors. A well-insulated floor can ensure better performance. Insulation Recommended Yes; under slabs or framed floors. Cork or similar on top of Concrete Subfloor as thermal break Indoor / Outdoor INTERIOR floor heating Application only. Embedded in Mortar only Installation On Sub Floor on TOP of Sub Floor (Plywood, backer board, concrete) Distance from Wax Ring at toilet flange Install 4 - 6 inches away; can be under front of toilet. Approx 20" from wall Trowel Size recommended minimum 3/8" x 1/4". Works for most ceramic tile; verify with tile/mortar manufacturer Trowel type Recommended Heavy Duty Plastic PRO-Trowel Cut Warning No. Never cut the heating elements to shorten Minimum Installation Temperature 50 Degrees F / 10 Degrees C
- More Details
Warranty from Manufacturer 25 years Heated Area Size Covered 85 Amp Draw 8.6 Total Watts 1020 watts Installation Style Heating Cable secured to floor using cable guides (track). Guides are secured to floor with tape, screws or glue. Custom Size Options None. Standard lengths only. No customization Cable strap or guides Cable guides are included in the kit Acceptable Floor Coverings Tile, Stone,Granite, Marble, Slate, Engineered wood, Laminate Made In USA Made in Canada from a majority of USA components.