The SunTouch Watts Radiant ProMelt Digital DualTemp P-3285s thermostat is a Non-programmable heat-only thermostat with the ability to monitor surface temperature (using floor sensor 500802 sold separately) and works in conjunction with a CP Panel for outdoor patio heating. This Stat is also used for indoor hydronic heating
The DualTemp is manually set to maintain a desired floor temperature with a min/max floor temperature range. Simple to set and operate, the Floor (patio surface) temperature are adjustable from 41 degrees F to 99 degrees F. The Digital DualTemp also includes a manual 7 degree F temperature setback feature.
The 24v DualTemp is a three-wire thermostat. It must be powered from the same external 24-VAC transformer that powers the relay coil built-in to the CP-series of panels. It does not operate alone or on line voltage power.
This thermostat must be mounted INDOORS and the sensor wire run to the outdoor surface that is to be heated/monitored. Since it operates on 24v, the DualTemp P-3285 must be used in conjunction with a Contactor Pro panel to control a patio heating system.
Remember to order the floor sensor 500802 separately.
- Low voltage operation (24 VAC) and is powered by the CP series panels
- Connection to a ProMelt CP panel allows control of 250 - 1250 Sq Ft of patio heating, or more.
- Simple push button operation
- Compact size
Brand Name SunTouch Floor Warming Voltage No Visible Depth No Inside Box Width No Inside Box Height No Inside Box Depth No LCD Display Size Ht No LCD Display Size Width No Dial Size (diameter) No Manufacturer Watts Radiant Controls/Thermostat is required for operation No
- Instructions + Video
Instructions + Video
Instruction Manual SunTouchP-3285 DualTemp Air/Floor Thermostat, 24V (Patio Heating Only) Installation Manual Install Steps
- To mount the thermostat, remove the thermostat cover by removing the white Screw Cover (located in the center of the thermostat cover) and the Cover Screw.
- Secure the Base Unit to the wall. Be sure to feed the electrical wiring (18-3 or 18-4) through the provided slot in the Base Unit and connect to appropriate terminal block(s).
- Replace the Cover, Cover Screw and Screw Cover.
- If floor sensing is desired, be sure to order the 500802 sensor; then connect floor sensor to the corresponding floor sensor terminals (labeled NTC, the first two terminals on the right terminal block).
Electrical Box Recommended Size No Width No Height No Depth No Unit and wires protrude into box No Floor Sensor Included No Floor Sensor Length Ft No Floor Sensor Length Meters No Floor Sensor Type No Floor Sensor Resistance Range (@ 20,000) No Floor Temperature Sensing Primary No Ambient Air Temperature sensing Mode No Ambient Air w/ Floor Temp option No Location / Use : Indoor Only Outdoor Only Outside temp and humidity sensor option (purchased separately) No GFEP / GFCI Protection (Ground Fault Circuit Interrupter) No Skill Level No Installation Layout Map customized for my project No
- More Details
Why Helps No Warranty from Manufacturer No Remote Control Compatible No Control Multiple areas No Remote control Mode No Home Automation Integration No Smart Technology/Early Start No Manual Temperature Override Possible No On/Off Switch for complete shutdown @ end of heating season No Regulator Mode option No Heating Cycle length No Safety Listing No Canadian Electric Code reference No National Electric Code reference No Programming Method No Packaging No Pre-Loaded program options No User Settable program No 7 Day Prog (Su - Sa) No 5-2 Program (M-F + S-S) No 5 - 1 - 1 Prog (M-F - Sa - Su) No Programming Saved Indefinitely (or number of hours) No Time / Date settings retained during power outage No No Battery Required No Minimum Display Temp No Maximum Display Temp No Accuracy Degrees F No Floor sensor Connection No Electrical Connections No Operating Temperature Range (degrees F) No Minimum Setting Temp No Maximum Setting Temp No Click here to see all discontinued Thermostats No Benefits No Made In USA Made in USA