WarmWire is a more affordable alternative to floor heating mats that performs wonderfully in any room of your home or office under tile, natural stone, laminate, engineered woods, carpet, vinyl, & linoleum. (Consult flooring manufacturer for additional information on compatibility with radiant floor heating.)
• Total design freedom allows for installation around turns & obstructions such as a toilet or kitchen island
• Installs with traditional strap or membrane at 2 ½, 3, or 3 ½ inch spacing
• Approved for shower installation where permitted by the local authority having jurisdiction (AHJ)
• 25-year manufacturer warranty whether installed with CableStrap or another manufacturers’ membrane
Plan your layout and determine the cable direction. Measure
about 3" in. inches from the wall, and place strap parallel to
the wall. Under toe kick spaces, install the strap 1.5"in. inches
to 2" in. inches away from the vanity.
Cut the strap to length for each side of area
to be heated.
Secure the strap to the subfloor using double-sided
tape, glue, or fasteners.
Fill in each section back and forth with cable,
spacing the wire 2.5" or 3" in. inches
apart. For additional areas, cut and attach the
straps accordingly and begin weaving the
wire into that area.
If cables are running greater than 3' or 4'ft. feet across a room, be sure to add another
strap to thread through in the center of the area to be heated.
Yes, can be installed in a tiled shower. UL listed, verify local code.
INTERIOR floor heating application only. Embedded in mortar or self leveler only
|Mats or Wire||Supply Wire||Breaker|
|120||up to 12 amps||14||1||single pole||15 or 20 A|
|120||up to 15 amps||12||1||single pole||20 A|
|240||up to 12 amps||14||1||double pole||15 or 20 A|
|240||up to 15 amps||12||1||double pole||20 A|
* Recommended only. Follow local codes for wire gauge size.
20 A Breaker.
Blue Flexible Polyurethane WaterProof Jacket surrounding 2 ETFE insulated copper heating wires, metal jacket & ground wire drain
Install 4 - 6 inches away; can be under front of toilet. Approx 20" from wall
Minimum 3/8" x 1/4". Dependent on tile size - verify with tile/mortar manufacturer
50° Degrees F / 10° Degrees C
|Safety Listing||UL (Underwriters Laboratory) Listed for U.S. and Canada under UL 1673 and CAN/CSA C22.2 No. 130-03, File No. E185866|
|Cable Length (inches)||1404"|
|Cable Length (meters)||35.7 m|
|Heated Area Size Covered||30|
|Wattage per SF||12|
|Total Watts||360 watts|
|Heating Power Output per Hour (BTU)||41 BTU per Sq Ft/Hour @ 3" in. inch spacing|
|Heating Power Output Total||1230 BTU total|
|Spacing of Heating Wire||2.5" - 3" - 3.5" on center|
|Power Lead Length||10 Feet|
|Power Lead Wire Gauge||18 AWG|
|Power Lead Type||Armored, NEC color code, Single point connection at 1 corner of mat. No return wire like inferior products|
|Thickness||.110" - .132" (nominal) Shorter cables are thinner.|
|Ohms Reading (resistance value)||33-42|
|EMF (Electro Magnetic Field)||Yes. Verified by Independent Testing Laboratory as ultra low.|
|What's In The Box||WarmWire Spool in Easy to dispense box. Detailed Installation Manual. Installation video online.|
|Warranty from Manufacturer||25 year warranty backed by USA Manufacturer since 1873|
WarmWire = Zero EMF
Electromagnetic fields (EMF) are generated by all electrical devices, and the possible dangers of exposure to EMF are still the subject of debate and scientific research. Out of concern for their customers' safety, SunTouch created the first EMF-canceling electric radiant floor heating system in 1993, and to this day they only manufacture and sell floor heating systems that use their patented EMF-canceling design. We provide this EMF information because it is important to some people, not to frighten you or exaggerate any risk like others do. We simply aim to inform you and leave the choice up to you after explaining what we know. Read More Here.
|Acceptable Floor Coverings||Natural Stone,Tile, Laminate, Engineered Woods, Carpet, Vinyl, Linoleum, Solid Hardwood (if you use sleepers)|
|Spacing between runs 1||2.5|
|Spacing between runs 2||3|
|Spacing between runs 3||3.5|
|Heated SF 1||25|
|Heated SF 2||30|
|Heated SF 3||36|
|Watts Per SF 1||14.4|
|Watts Per SF 2||12|
|Watts Per SF 3||10.3|